PCI ControlKeeper Touch Logic Board
This component can be used in the ControlKeeper Touch and ControlKeeper relay panels.
If used in the ControlKeeper panels, then you must replace the ControlKeeper Keypad Logic Card with a Touchscreen Logic Card and replace the Override Card at the same time.
If used in the ControlKeeper Touch panels, then you can replace the Logic Card and Override Card individually.
Connecting Low Voltage Inputs
The ControlKeeper T logic board can support a total of 64 switch inputs. Of these 64 inputs, 32 of them may be dry contact closure inputs that are connected to the terminal blocks at the bottom of the ControlKeeper Logic Board. Digital switch inputs may also be used on the ControlKeeper. If no contact input type switches are being used, the full 64 switch inputs may consist of digital switches. If a combination of contact input switches and digital switches are being used, the combined total cannot exceed 64 inputs. The ControlKeeper T Logic Board can support a total of 4 analog inputs. The logic board contains 32 software analog inputs to allow these four physical analog inputs to be programmed at different switching thresholds to achieve the multi threshold application from a single analog input. Regardless of input type used, it is recommended that all input wiring be done prior to applying power to the logic board or at the very least with the terminal blocks removed from the logic board. Please verify that there are no shorts to AC ground prior to connection of input devices