Leviton Colortran iSeries i48E/96E Quad Control Module, REPAIR (A Repair requires that you ship out your malfunctioning unit, per instructions provided via email.)
Part #CTP-4-0311e, repair.
Part #IECM0-001-148, repair.
This is the repair of an existing Leviton Colortran iSeries i48E/96E Quad Control Module control module.
Once you place the order, we will send you an RMA# and shipping instructions to ship your control module for repair.
The control module will be repaired within 2-business days of receipt and then overnight return shipped to you.
It is your responsibility to ship the control module out for the repair according to the directions provided.
If you need assistance removing your control module from the dimmer rack, then please call us at 1-866-567-5937.
The control module contains nearly all of the control electronics and generates the necessary control signals and power necessary to control the dimmers in the rack. There are 2 different control modules for i series e and i series quad. · The i96/48 control module (CTP-0311e) controls i96e, i48e or i48Quad dimmer racks in all configurations. · The i24 control module (CTP-0313e) controls i24 dimmer racks in all configurations. Control modules are completely interchangeable within the i series e and i series quad system, as long as they are the same type of control module as detailed above. The only selection that makes a control module unique is the thumbwheel address setting on the front of the control module. All other individual parameters for the rack are stored in the socketed serial EEPROM chips on the i series e backplane. On power up, the control module automatically loads all the unique information from the serial EEPROMS on the backplane, determines the line frequency, and phase angle firing assignments. The top pair of chips in a 16 pin DIP socket (P5) permanently store all the unique information for the upper control module position. The bottom pair of chips in a 16 pin DIP socket (P6) permanently store all the unique information for the lower control module position. The unique information that is stored is the configuration parameters of the control module itself, backup looks, analog submaster scenes, the panic scene, and the custom patch. Standard patches are available by setting the address number in the range of ‘1 ‘to ‘15’. Setting the thumbwheel to ‘0’ invokes the custom patch stored in the EEPOMS on the backplane.